Since 1985, Force Home Services is your best choice for repair, installation, and service in homes and buildings just like yours in the Northern DFW, Denton, and Collin Counties. We take special pride in the craftsmen we train and employ--a fact you'll see in the reviews below. It's also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that Force Home Services stands behind the work we do as well as complies with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Plumbing, & Heater Repair in Pilot Point, TX. Call us today at (940) 323-1051!
The technician was able to look at the issue and repair the same day I called in.
The serviceman was polite, answered questions, allowed me to tag along & watch
Performing maintenance on four air conditioning systems
Fall club maintenance
Charge system to manufacture specs performed leak search carrier pilot point
Loud noise. High static pressure due to pelted filter
Fall tune up
Performing one system spring ac maintenance club members
Install t stat
diagnosed and repaired/adjusted water heaters, repaired hallway toilet, diagnosed hallway tub leak, cleared kitchen sink drain
Spring tune up. Replaced capacitor and contractor
Before AC spring tune-up on a day and night heat pump and a 2009 Rheem heat pump
Perform Comfort club spring maintenance on 2006 Carrier heat pump
Performed two system spring club maintenance
Performed one system spring club maintenance on carrier heat pump air handler found no major repairs necessary reccomended secondary safety switch and secondary drain line ran out of house
Replaced a primary circuit board
Installed a UV light and cleaned an evaporator coil.
Fixed a loud noise coming from the blower motor.
Diagnosed spark ignitor bad on gas fireplace
Single system fall club member heating tune up in pilot point texas
repaired a fan motor/ blade that was out of balance.
2 system a_c_t up on 2 year old carrier units in pilot point texas
2 system spring tune up in Pilot Point Texas
thermostat check out in pilot Point Texas
Cleared ac condensate line